RADIK PLAN VKL is a panel radiator in PLAN design and in VENTIL KOMPAKT version which allows left bottom connection to a pressurized heating system. There are two upper and two lower hangers welded at the back side of the radiator. Radiators in length 1 800 mm and more have six hangers.
300, 400, 500, 600, 900 mm
400, 500, 600, 700, 800, 900, 1000, 1100, 1200, 1400, 1600, 1800, 2000 mm
- Type 11 PLAN VKL
- Type 21 PLAN VKL
- Type 22 PLAN VKL
- Type 33 PLAN VKL
6 × G½ inside
Highest allowed working pressure
Highest allowed working temperature (°C)
In case of two-pipe heating system it is necessary to calculate the correct level of valve presetting and specify this in the project documentation to ensure a proper function of the heating system. This must be kept by the installer during installation of the heating system.
In case of one-pipe heating system it is necessary to set the valve at level 6. For adjusting the required mass flow in the radiator we recommend to use the compact connecting fitting with a fixed or adjustable flow volume of water in the radiator.